Analysis of a Harmonics Neutralized 48-Pulse STATCOM with GTO Based Voltage Source Converters

- Journal title : Journal of Electrical Engineering and Technology
- Volume 3, Issue 3, 2008, pp.391-400
- Publisher : The Korean Institute of Electrical Engineers
- DOI : 10.5370/JEET.2008.3.3.391

Title & Authors

Analysis of a Harmonics Neutralized 48-Pulse STATCOM with GTO Based Voltage Source Converters

Singh, Bhim; Saha, Radheshyam;

Singh, Bhim; Saha, Radheshyam;

Abstract

Multi-pulse topology of converters using elementary six-pulse GTO - VSC (gate turn off based voltage source converter) operated under fundamental frequency switching (FFS) control is widely adopted in high power rating static synchronous compensators (STATCOM). Practically, a 48-pulse ( pulse) configuration is used with the phase angle control algorithm employing proportional and integral (PI) control methodology. These kinds of controllers, for example the compensator at Inuyama switching station, KEPCO, Japan, employs two stages of magnetics viz. intermediate transformers (as many as VSCs) and a main coupling transformer to minimize harmonics distortion in the line and to achieve a desired operational efficiency. The magnetic circuit needs altogether nine transformers of which eight are phase shifting transformers (PST) used in the intermediate stage, each rating equal to or more than one eighth of the compensator rating, and the other one is the main coupling transformer having a power rating equal to that of the compensator. In this paper, a two-level 48-pulse STATCOM is proposed where eight, six-pulse GTO-VSC are employed and magnetics is simplified to single-stage using four transformers of which three are PSTs and the other is a normal transformer. Thus, it reduces the magnetics to half of the value needed in the commercially available compensator. By adopting the simple PI-controllers, the model is simulated in a MATLAB environment by SimPowerSystems toolbox for voltage regulation in the transmission system. The simulation results show that the THD levels in line voltage and current are well below the limiting values specified in the IEEE Std 519-1992 for harmonic control in electrical power systems. The controller performance is observed reasonably well during capacitive and inductive modes of operation.

Keywords

Fundamental frequency switching;Gate-Turn off thyristor;Phase shifting transformer;Total harmonic distortion;Voltage source converter;

Language

English

Cited by

1.

2.

3.

4.

References

1.

E. J. Stacey, "Simplified quasi-harmonic neutralized high power inverters," U. S. Patent 4 870 557, Sept. 26, 1989

2.

C. D. Schauder, "Advanced Static VAR Compensator Control System," U. S. Patent 5 329 221, Jul. 12, 1994

3.

S. Mori, K. Matsuno, T. Hasegawa, S. Ohuichi, M. Takeda, M. Seto, S. Murakami, and F. Ishiguro, "Development of a large static VAR generator using self-commutated inverters for improving power system," IEEE Trans. on Power Systems, vol. 8, no. 1, pp. 371-377, Feb. 1993

4.

C. Schauder, M. Gernhardt, E. Stacey, T. Lemak, L. Gyugyi, T. W. Cease, and A. Edris, "Development of a ${\times}100$ MVAr static condenser for voltage control of transmission systems," IEEE Trans. on Power Delivery, vol. 10, no. 3, pp. 1486 -1496, July 1995

5.

C. K. Lee, Joseph S. K. Leung, S. Y. Ron Hui, and Henry Shu-Hung Chung, "Circuit-level comparison of STATCOM technologies," IEEE Trans. on Power Electronics, vol. 18, no. 4, pp. 1084-1092, July 2003

6.

G. C. Cho, G. H. Jung, N. S. Choi, and G. H. Cho, "Analysis and controller design of static VAR compensator using three-level GTO inverter," IEEE Trans. on Power Electronics, vol. 11, no. 1, pp. 57-65, Jan. 1996

7.

J. E. Hills and W. T. Norris, "Exact analysis of a multipulse shunt converter compensator or STATCOM Part-I and II: Performance," IEE Proc. Generation, Transmission and Distribution, vol. 144, no. 2, 1997, pp. 213-218 and 219-224

8.

C. Schauder, M. Gernhardt, E. Stacey, T. Lemak, L. Gyugyi, T. W. Cease, and A. Edris, "Operation of ${\timex}100$ MVAR TVA STATCON," IEEE Trans. on Power Delivery, vol. 12, no. 4, pp. 1805-1811, Oct. 1997

9.

K. K. Sen, "Statcom - static synchronous compensator: theory, modeling, and applications," IEEE PES WM 1999, vol. 2, pp. 1177-1183

10.

C. Schauder, L. Gyugyi, E. Stacey, M. Lund., L. Kovalsky, A. Keri, A. Mehraban, and A. Edris, "AEP UPFC project: installation, commissioning and operation of the ${\timex}160$ MVA STATCOM (phase-I)," IEEE Trans. on Power Delivery, vol. 13 no. 4, pp. 1530-1535, Oct. 1998

11.

Y. H. Liu, J. Arrillaga, and N. R. Watson, "Multi-level voltage reinjection - a new concept in high voltage source conversion," IEEE Proc., Generation Transmission and Distribution, vol. 151, no. 3, 2004, pp. 290-298

12.

Y. H. Liu, J. Arrillaga, and N. R. Watson, "STATCOM performance of a multi-level voltage reinjection converter," IEEE/PES Transmission and Distribution Conference & Exhibition: Asia and Pacific, 2005

13.

M. S. El-Moursi, and A. M. Sharaf, "Novel Controllers for the 48-Pulse VSC STATCOM and SSSC for voltage regulation and reactive power compensation," IEEE Trans. on Power Systems, vol. 20, no. 4, pp. 1985-1987, Nov. 2005

14.

Y. H. Liu, R. H. Zhang, J. Arrillaga, and N. R. Watson, "An overview of self-commutating converters and their application in transmission and distribution," IEEE/PES Trans. and Distrib. Conf. & Exhibition: Asia and Pacific, 2005

15.

K. R. Padiyar and Nagesh Prabhu, "Design and performance evaluation of sub-synchronous damping controller with STATCOM," IEEE Trans. on Power Delivery, vol. 24, no. 3, pp. 1395-1405, July 2006

16.

A. Jain, K. Joshi, A. Behal, and N. Mohan,"Voltage regulation with STATCOMs: modeling, control and results," IEEE Trans. on Power Delivery, vol. 21, no. 2, pp. 726-735, Apr. 2006

17.

B. K. Panigrahi, M. K. Mallick, and S. S. Dash, "A novel fuzzy logic controller for STATCOM to improve power system stability," Int. Journal of Automation and Control, vol. 1, no. 1, pp. 4-15, 2007

18.

B.-S. Chen and Y.-Y. Hsu, "An analytical approach to harmonic analysis and controller design of a STATCOM," IEEE Trans. on Power Delivery, vol. 22, no. 1, pp. 423-432, Jan. 2007

19.

W. Pan, J. Zhang, H. Chen, Y. Chang, and C. Wang, "Novel configuration of 60 pulse voltage source converter," IEEE PES GM, 2007

20.

N. Voraphonpiput, I. Ngamroo, and S. Chatratana, "Control system design for a STATCOM using complex transfer function," WSEAS Int. Conf. Proce. on Instrumentation, Measurement, Circuits & System, 2007, pp. 186-192

21.

Z. Xi, and S. Bhattacharya, "STATCOM operation strategy under power system faults," IEEE PES GM, 2007

22.

IEEE Std. 519-1992, IEEE Recommended Practices and Requirements for Harmonic Control in Electric Power Systems