Simulations of the Dynamic Load in a Francis Runner based on measurements of Grid Frequency Variations

Title & Authors
Simulations of the Dynamic Load in a Francis Runner based on measurements of Grid Frequency Variations
Ellingsen, Rakel; Storli, Pal-Tore;

Abstract
In the Nordic grid, a trend observed the recent years is the increase in grid frequency variations, which means the frequency is outside the normal range (49.9-50.1 Hz) more often. Variations in the grid frequency leads to changes in the speed of rotation of all the turbines connected to the grid, since the speed of rotation is closely related to the grid frequency for synchronous generators. When the speed of rotation changes, this implies that the net torque acting on the rotating masses are changed, and the material of the turbine runners must withstand these changes in torque. Frequency variations thus leads to torque oscillations in the turbine, which become dynamical loads that the runner must be able to withstand. Several new Francis runners have recently experienced cracks in the runner blades due to fatigue, obviously due to the runner design not taking into account the actual loads on the runner. In this paper, the torque oscillations and dynamic loads due to the variations in grid frequency are simulated in a 1D MATLAB program, and measured grid frequency is used as input to the simulation program. The maximum increase and decrease in the grid frequency over a 440 seconds interval have been investigated, in addition to an extreme event where the frequency decreased far below the normal range within a few seconds. The dynamic loading originating from grid frequency variations is qualitatively found by a constructed variable $\small{T_{stress}}$, and for the simulations presented here the variations in $\small{T_{stress}}$ are found to be around 3 % of the mean value, which is a relatively small dynamic load. The important thing to remember is that these dynamic loads come in addition to all other dynamic loads, like rotor-stator interaction and draft tube surges, and should be included in the design process, if not found to be negligible.
Keywords
Language
English
Cited by
References
1.
Nielsen, T. K. and Storli, P.-T. 2014, "Measurements and simulations of turbines on a common grid", IOP Conference Series: Earth and Environmental Science, Vol. 22

2.
Statnett, 2014, "Systemdrifts- og Markedsutviklingsplan 2014-2020. Tiltaksplan for sikker og effektiv drift av krafverksystsemet"

3.
Eurelectric and Entso-E, 2011,"Deterministic frequency deviations - root causes and proposals for potential solutions", A joint EURELECTRIC - ENTSO-E response paper

4.
Storli, P.-T. and Nielsen, T.K., 2014, "Dynamic load on a Francis turbine runner from simulations based on measurements", IOP Conference Series: Earth and Environmental Science, Vol. 22

5.
Chapman, S., 2005, Electric Machinery Fundamentals, McGraw-Hill Companies, Incorporated

6.
Nielsen, T. K., 1996, "Dynamic Behaviour of Governing Turbines Sharing the Same Electrical Grid", 18th IAHR Symposium on Hydraulic Machinery and Cavitation, Valencia, Kluwer Academic Publisher