- Volume 17 Issue 1
Concern about green water problem has surfaced as a serious issue in Korea. In order to solve this problem, it is necessary to research inhibition of green water and corrosion control of copper pipe in water service. This paper discovered that moderate corrosion inhibitors can solve the green water problem and copper corrosion in water service by adding the optimal concentration of corrosion inhibitors based on regulation. Firstly, in the case of phosphate based corrosion inhibitors, as dosage of the corrosion inhibitor increases from 1 mg/L to 5 mg/L, the relative effect of corrosion inhibitor declines rapidly. Secondly, except for 1 mg/L dosage of silicate based inhibitor, relative effects of the inhibitor displays a positive number depending on inhibitor concentration. The most significant result is that the amount of copper release shows a downward trend, whereas the phosphate based inhibitor accelerates copper ion release as the inhibitor dosage increases. Thirdly, as the dosage of mixed inhibitors increases to 10 mg/L, the copper release change shows a similar trend of phosphate based inhibitor. Lastly, according to the Langelier saturation index (LI), silicate based inhibitors have the most non corrosive value. Larson ratio (LR) indicates that phosphate based inhibitors are the least corrosive. Korea water index (KWI) represents that silicate based inhibitors are most effective in controlling copper pipe corrosion.
Copper release;Corrosion control;Green water;Korea water index;Phosphate based inhibitors;Silicate based inhibitor
- American Water Works Association (AWWA). Internal corrosion of water distribution systems: cooperative research report. 2nd ed. Denver: AWWA Research Foundation; 1996.
- McIntyre P, Mercer AD. Corrosion and related aspects of materials for potable water supplies. London: Institute of Materials; 1993.
- Xiao W, Hong S, Tang Z, Seal S, Taylor JS. Effects of blending on surface characteristics of copper corrosion products in drinking water distribution systems. Corros. Sci. 2007;49:449-468. https://doi.org/10.1016/j.corsci.2006.04.018
- Goh KH, Lim TT, Chui PC. Evaluation of the effect of dosage, pH and contact time on high-dose phosphate inhibition for copper corrosion control using response surface methodology (RSM). Corros. Sci. 2008;50:918-927. https://doi.org/10.1016/j.corsci.2007.12.008
- Wells B; Water Services Association of Australia. Review of remedial treatments for copper corrosion by-product release (blue water), pitting and cuprosolvency. Melbourne: Water Services Association of Australia; 2000.
- Na SC. Study on corrosion protection technology of copper pipe for potable water supply [master's thesis]. Incheon: Inha University; 2007.
- Edwards M, Hidmi L, Gladwell D. Phosphate inhibition of soluble copper corrosion by-product release. Corros. Sci. 2002;44:1057-1071. https://doi.org/10.1016/S0010-938X(01)00112-3
- Sheiham I, Jackson PJ. Scientific basis for control of lead in drinking water by waer treatment. J. Inst. Water Eng. Sci. 1981;35:491-515.
- Lee HD, Gwak PJ, Lee JE, Kim YG. Water quality monitoring for corrosion control in waterworks system. J. Korean Soc. Water Wastewater 2009;23:77-87.
- American Water Works Association. Water quality and treatment: a handbook of community water supplies. 4th ed. New York: McGraw-Hill; 1990.