- Volume 23 Issue 4
DOI QR Code
Improvement of Rapid Sand Filtration to Two Stage Dual Media Filtration System in Water Treatment Plant
정수처리장 사여과지의 이단이중여과재 시스템으로의 개량
Woo, Dal-Sik;Kim, Jooneon;Hwang, Byung-Gi;Chae, Su-Kweon;Jo, Kwanhyung
- Received : 2014.01.21
- Accepted : 2014.04.21
- Published : 2014.04.30
This study aimed for evaluating the applicability of the two stage dual media filtration system in field water treatment plant. The field plant of two stage and dual media filtration system was operated for 2 months. Average iron concentrations of the settled water, existing filtered water and second stage filtered water was 0.041 mg/L, 0.007 mg/L and 0.005 mg/L, respectively. Removal efficiency of iron concentration in the second stage is appropriately 35% more than in existing filtered water. Also removal efficiency of residual chlorine in the dual media filtration system is relatively 42.3% more than in existing filtered water due to adsorption of activated carbon, but the removal of ammonia nitrogen by adsorption is insufficient. Average concentrations of THM and chloroform in the settled water are 0.033 mg/L, 0.026 mg/L, respectively and in existing filtered water are 0.023 mg/L and 0.023 mg/L. Average concentrations of THM and chloroform in the dual media filtration system are 0.008 mg/L and 0.013 mg/L. Therefore removal efficiency of THM concentration in second stage is more than 66.4% in existing filtrated water. Also removal efficiency of chloroform in the dual media filtration system is more than 50.0% in existing filtered water because of the adsorption of activated carbon. In this case backwashing period in dual stage system is 4~5 days, but in existing filtration system is 1~2 days.
Sand filtration;Two stage;Dual media;GAC;DBPs;Backwashing
- APHA, AWWA, WEF, 1998, Standard Method for the Examination of Water and Wastewater, 20th ed., Washington, DC.
- Boorman, G. A., Dellarco, V., T., Dunnick, J. K., Chapin, R. E., Hunter, S., Hauchman, F., Gardner, H., Cox, M., Sills, R.C., 1999, Drinking water disinfection byproducts: Review and approach to toxicity evaluation, Env. Health Persp., 107(Suppl 1), 207-217. https://doi.org/10.1289/ehp.99107s1207
- Jo, K. H., Kim, P. C., Woo, D. S., Cho, Y. T., 2002, The characteristics of chloramine formation and decay with pH variation, Kor. J. Env. Sci., 11(4), 347-353. https://doi.org/10.5322/JES.2002.11.4.347
- Kim, C. H., Kim, H. S., 2003, International seminar on membrane filtration technology for water supply, J. Kor. Soc. Wat. Waste., 17(5), 594-605.
- Kim, J. K., Jeong, S. G., Shin, C. S., Cho, H. J., 2005, Characteristics of disinfection by-products formation in Korea, J. Kor. Soc. Wat. Waste., 19(3), 301-311.
- Kim, S. S., Lee, K. H., 2005, Assessment and optimization of granular activated carbon (GAC) process in water treatment process, J. Kor. Soc. Wat. Waste., 19(6), 781-790.
- Lee, Y. J., Jo, K. H., Choi, J. H., Myung, B. T., Nam, S. H., 2001, Evaluation of chlorine demand and chlorine decay kinetics for drinking water, Kor. J. Env. Health Sci., 27(1), 27-35.
- Ministry of Environment, 2012, Standard for water treatment woks, Korea Water and Wastewater Works Association.
- Page, T., Harris, R. H., Epstein, S. S., 1976, Drinking water and cancer mortality in Louisiana, Science, 193, 55-57. https://doi.org/10.1126/science.935854
- Rook, J. J., 1974, Formation of haloforms during chlorination of natural water, J. Wat. Treat. Exam., 23(2), 234-243.
- US EPA, 1995a, Determination of Organic Compounds in Drinking Water, Method 502.2, Cincinnati, Ohio.
- US EPA, 1995b, Determination of Organic Compounds in Drinking Water, Method 551.1, Cincinnati, Ohio.
- Woo, D. S., Hwang, K. W., Kim, J. E., Hwang, B. G., Jo, K. H., 2011, Improvement of rapid sand filtration to two stage dual media filtration system in water treatment plant, Kor. J. Env. Health Sci., 37(2), 141-149. https://doi.org/10.5668/JEHS.2011.37.2.141
Supported by : 환경부, 국토해양부