- Volume 29 Issue 5
Although there are existing Residual Current Protective Device (RCD) including detect electric leakage and elements such as short circuit and surge, the occurrence of incidents caused by electric faults, including fire, are still constant. The purpose of this study is to analyze the causes of accidents through the electric field distribution in the interpretation of the fault contact breaker. Simulation results by the arc fault has shown the convergence of temperature and electric field to the defect. Through their simulation results, the main cause of erosion phenomena in circuit breaker bar is the electric arc by concentration of electric field not due to dissolve by temperature.
Power substation;RCD;Circuit breaker;Simulation;Electric field
- M. S. Han, Master's Thesis, p. 1, Seoul National University of Science and Technology, Seoul (2005).
- H. S. Kim, Master's Thesis, p. 1-14, Seoul National University of Science and Technology, Seoul (2010).
- D. K. Hwang, Master's Thesis, p. 1-3, Chungbuk National University, Cheongju (2012).
- J. S. Jung, Ph. D. Thesis, p. 3-4, Myongji University, Yongin (2011).
- Electrical Safety Portal System, Electrical Fire Statistics, http://www.esps.or.kr (2015).
- J. K. Choi, Master's Thesis, p. 1, Kangwon National University, Samcheok (2014).
- S. Knechi, B. Gonzalez, and K. Sieber, IEEE ISC. on TP, 329 (1996).
- W. H. Preece, Proc. Royal Soc., 36, 464 (1884). [DOI: http://dx.doi.org/10.1098/rspl.1883.0133]
- P.H.F. Morshuis, IEEE Trans. on DEI, 12, 905 (2005). [DOI: http://dx.doi.org/10.1109/TDEI.2005.1522185] https://doi.org/10.1109/TDEI.2005.1522185
- S. H. Jing, Master's Thesis, p. 8-23, University of Seoul, Seoul (2008).
Supported by : 인천대학교